Medford Wellington provides comprehensive heating, air conditioning, refrigeration, sheet metal, plumbing and electrical services to commercial and residential clients in Waltham, MA.
We are available for service 24 hours a day. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Waltham, MA.
for Waltham, MA
Commercial refrigeration repair for a Heatcraft reach-in cooler under a prep top for a unit not staying cool. Found product blocking the vents and preventing cold air from entering the unit.
Commercial HVAC repair for a Carrier providing no air, either warm or cold, to the area. Found unit completely down with error codes. Commercial HVAC install for new smoke detectors to prevent misreadings again.
Commercial heating repair for a Modine unit heater providing no heat to the space. Found burnt out contactors. Commercial heating install for new contactors and wiring to bring the unit back up to 100% functionality.
Commercial refrigeration repair for a Heatcraft walk-in freezer with condensation dripping from the evaporator coil. Found leak in coil. Commercial refrigeration install for a new evaporator coil.
Commercial refrigeration repair for a Delfield Walk-In Cooler that is completely down. Found Compressor relay tripped due to low pressue due to leak in compressor. Commercial refrigeration install for a new compressor on the unit.
Commercial refrigeration repair for a Randell Reach-In Cooler that is pooling water. Found clogged drain pan. Cleared drain pan and unit is operating at 100% with no extra water
Commercial HVAC repair for a hood vent and Make Up Air that is blowing cold air into the kitchen area. Found filters clogged on MUA 1 and MUA 2. Chemically cleaned and reinstalled filters and both units are at full operational status.
Commercial Heating Repair call for a Carrier packaged unit providing no heat. Commercial HVAC service needed for parts department.
Commercial HVAC Service call for a Lennox packaged RTU providing no heat to the office
Commercial Refrigeration Service call for a Trenton condensing unit on a walk-in refrigerator. Commercial HVAC service call for a Lennox RTU
Commercial Refrigeration Service call for a American Panel Walk-In Cooler
Commercial Refrigeration installation call for an American Pacific Walk-In Cooler needing a new door handle
Refrigeration call for a Federal Reach-In refrigerator not cooling with a leak. Installed ordered parts, charged unit, and unit pulled down to temp and cycled off. Call is complete.
Refrigeration call. 4 Drawer low boy under pasta station at 28 degrees. Evaporator and drain pan fully and evenly iced up. Manual initiated defrost. Condenser coil and cover plugged with grease. Chemically cleaned coil and cover several times. Also replaced prefilter. Drawer gaskets and rollers good. Kitchen ambient temperature comfortable. Box at 25 and dropping. Call is complete.
Refrigeration call. Found thermostat set to cold and adjusted temperature to -8f with a 4 degree diff. Call is complete.
HVAC call. Gained access to the roof and located new Lennox RTU. No power at prodigy board. Checked disconnect, which had power. Found line wire at compressor contactor middle pole had popped out from contactor. Middle pole was burnt up. Replaced contactor and tested operation. RTU is now operational. Call complete.
Refrigeration call. Nine door freezer was in the low 20s. Ice cream was melting. Checked evaporator coil and found no ice. Liquid line was cold. Located temp control and found that Ranco ETC was set for 20 degrees F with a differential of 5. Setting was way too high. Set temp control for -10F with 5 degree diff. Set up ladder and accessed condensing unit on roof. Sight glass was full and operation was good. Freezer is at 2 degrees and dropping. Job complete.
HVAC Service call. Preventative Maintenance service completed per contracted agreement. All requirements per seasonal obligations have been met. Any issues found during PM service have been brought to the attention of the appropriate personnel and have been defined as either a critical or a non critical issue for their review. HVAC call is complete.
Arrived on site . Checked in with office manager who explained where water has been seen around the Ice Machine. Opened up panels, no water stains inside machine. Drained and filled reservoir to ensure it is not overflowing. Checked drain and supply connections, both were somewhat loose. Tightened hose clamp on drain and tightened braided hose for supply. Poured water down drain, no leaks from drain hose. Unit operational, refrigeration call is complete.