Medford Wellington provides comprehensive heating, air conditioning, refrigeration, sheet metal, plumbing and electrical services to commercial and residential clients in Salem, MA.
We are available for service 24 hours a day. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Salem, MA.
for Salem, MA
Commercial HVAC Repair for an AAON RTU that is not cooling the space. Found the Indoor Blower motor to have failed. Recommended Commercial HVAC Install for a new Indoor Blower motor.
Refrigeration call for a True Reach In Freezer
Site survey for a Preventative Maintenance contract.
HVAC Service call. Preventative Maintenance service completed per contracted agreement. All requirements per seasonal obligations have been met. Any issues found during PM service have been brought to the attention of the appropriate personnel and have been defined as either a critical or a non critical issue for their review. HVAC call is complete.
HVAC call. Customer reports not all areas receiving AC/Air. Tested each damper for power and operation. Found a few dampers seized and manually opened. Once air flow went to the trunks that were closed off the temp began to improve in the warm spots. Used the manual dampers at the end of each trunk to balance the air flow based on user preference for the area the diffuser was cooling. The space came down to 70 deg after I made adjustments. Ill follow up on Tuesday and if any areas need minor adjustments ill make them at that point. Call is complete.
HVAC call. Condenser unit was off on arrival. Found oil pressure switch was tripped. Reset switch and checked operations. Call is complete.