Medford Wellington provides comprehensive heating, air conditioning, refrigeration, sheet metal, plumbing and electrical services to commercial and residential clients in Lowell, MA.
We are available for service 24 hours a day. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Lowell, MA.
for Lowell, MA
Great work by the plumbers!
Dexter Caulfield - Lowell, MA
I recently had a full conversion from Oil to Gas done by the plumbers at Medford Wellington and they did a tremendous job. Mario and Max ran new piping that looks great and is out of the way and got everything up and running in a timely manner. The new burner on our Steam Furnace looks and works great! Thank you!
Commercial Refrigeration repair on a Nor-lake walk in cooler that was not shutting properly. Found door sweep to be a little to long and covered in debris. Recommended commercial Refrigeration repair to cut a little of the door sweep and to clear the debris in to sweep
Commercial Hvac repair for a Bryant AHU that produce any cold air. Found blower motor to be fried. Recommended commercial Hvac repair to replace the blower motor.
Commercial Hvac Repair for a Mitsubishi mini split that runs but won't produce any cooling. Found Condenser coil to be covered in leaves and debris also found evaporator coil to be frozen solid as well. Recommended Commercial Hvac repair to remove the leaves and chemically clean the coil as well as cleaning the air filters ant the evaporator. coil.
Commercial Refrigeration Repair on a Hoshizaki Ice Machine that was just pumping water around but not producing any ice. Found the units overflow drain unscrewed and floating. Recommended commercial refrigeration repair to screw the overflow drain back in.
Commercial Air conditioning repair for a Lennox RTU that is running very loud. Found compressor to be disconnected from its housing and condenser fan to be lose. Recommended Commercial Air conditioning Repair to tighten the compressor and condenser fan.
Commercial Hvac Repair for a Lennox Condensing unit that was not Running. Found lose wires at the thermostat. Recommended Commercial Hvac Repair to tighten the screw.
Commercial Ac Repair for a Daikin mini split that was not running. Found compressor to have died. Recommended Commercial Ac Install for new Compressor.
Commercial Refrigeration Repair for a Beverage Air walk in cooler that was Not producing enough cooling. Found Condenser coil plugged with dirt and dust. Recommended Commercial Refrigeration Repair to clean the coil.
Commercial Refrigeration Repair for a Scotsman Ice machine Not producing ice. Found faulty power supply. Recommended Commercial Refrigeration Install for a new power supply.
Commercial Hvac Repair for a carrier RTU not supplying any cooling. Found Compressor to have died. Recommend Commercial Hvac Install for a new compressor.
Commercial air conditioning repair for a Lennox RTU that is sending no cold air to the main loading area. Found the RTU has a seizer fan that will not budge. Commercial air conditioning install for a new blower motor assembly.
Commercial refrigeration repair for a Hoshizaki Ice Machine that is currently producing no ice at all. Found the units condenser to be down. Commercial refrigeration install for a new ice machine condenser.
Commercial refrigeration repair for a Continental Reach-In Cooler that is making a lot of noise. Found the evaporator fan to be the cause, has broken fin. Commercial refrigeration install for a new evaporator fan.
Commercial HVAC repair for an AAON Heat Pump that is no longer sending any form of heat or AC to the rear office. Found the unit's power supply to have an issue. Commercial HVAC Install for a new power supply.
Commercial HVAC repair for a Carrier RTU that is providing no cool air to the kitchen area. Found the unit to have a leak in the Condenser. Commercial HVAC install for a new condenser.
Commercial air conditioning repair for a York RTU that is not functioning. Found the unit to have an issue with the control board and it is not responding. Commercial air conditioning install for a new control board.
Commercial Refrigeration repair for a True 2-door stand up reach-in cooler that is running warm. Found the evaporator coil to be very dirty and not allowing air to travel over them. Commercial Refrigeration install for a coil cleaning.
Commercial Refrigeration repair for a Manitowoc Ice Machine that is not making any ice. Took the unit apart and found that no water was coming in. Commercial Refrigeration install for a new water pump.
Commercial HVAC repair for a Bryant RTU that is providing little air to the rear office area. Found the fan belt to have stretched massively the fan is turning, but very very slowly. Commercial HVAC install for a new fan belt.
Commercial HVAC Repair for a Carrier RTU that is currently not responding to any requests for heat. Found the thermostat to be dead. Commercial HVAC install for a new thermostat unit.
commercial hvac repair for Daikin split system not running. found bad compressor. commercial hvac installation of new compressor
commercial hvac repair for for Bryant rtu not cooling. found bad blower motor. commercial hvac installation of new blower motor
commercial hvac repair for Trane rtu running warm. found bad compressor. commercial hvac installation of new compressor
commercial refrigeration repair for Bohn walk in cooler icing up. found restricted thermostatic expansion valve. commercial refrigeration installation of new txv
commercial hvac repair for Mitsubishi ductless split not keeping up. found bad condenser fan motor. commercial hvac installation of new condenser fan motor