Medford Wellington Services Co., Inc. provides complete air conditioning, heating and refrigeration services to the residents and businesses of Hartford, CT. we are available 24/7 to meet your services needs.
Read reviews from our commercial and residential clients in Hartford, CT to see why they consider us to be their trusted local HVAC and refrigeration contractor.
for Hartford, CT
HVAC service call for a Carrier Packaged RTU. While onsite replacing the exhaust fan I found the condenser coils to the two RTU completely plugged with pollen. I purchased some chemical cleaner and chemically cleaned both RTUs as well as the washable prefilters on the RTUs and MUA. Cleaned up and checked out. Call is complete.
HVAC Service call. Preventative Maintenance service completed per contracted agreement. All requirements per seasonal obligations have been met. Any issues found during PM service have been brought to the attention of the appropriate personnel and have been defined as either a critical or a non critical issue for their review. HVAC call is complete.
Ventilation call. Checked the breakers and did not find any breakers tripped. Located the switch and verified it was operating, and once I switched the switch back to the ON position I heard the fan turn on. Gained access to the roof and found the fan running. Removed the cover and verified the variable speed switch and capacitor were operating properly. The fan is getting the proper voltage and verified the fan was pulling close to the full load amps when in high speed, which it was. Removed the fan from the curb and verified there was no debris located in the blade. Contacted Captive Aire tech support and verified over the phone the fan was operating properly. Call is complete.
Preventative Maintenance is completed per contracted agreement. All requirements per seasonal obligations have been met. Any issues found during PM service have been brought to the attention of the appropriate personnel and have been defined as either a critical or a non critical issue for their review
HVAC Electric Unit Heater Heating Repair