Medford Wellington provides comprehensive heating, air conditioning, refrigeration, sheet metal, plumbing and electrical services to commercial and residential clients in Framingham, MA.
We are available for service 24 hours a day. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Framingham, MA.
for Framingham, MA
Commercial Hvac Repair for a York AHU not producing any cooling. Found Blower motor capacitor to be blown. Recommended commercial Hvac install to replace the capacitor.
Commercial Hvac repair for a AAON RTU that is not supplying enough cooling to the space. Found condenser coil to be plugged with debris. Recommended Chemically cleaning Condenser.
Commercial Air conditioning repair for a LG mini split that is leaking all over the place. Found drain pan to be plugged. Recommended commercial Air Conditioning repair to unclog the drain pan.
Commercial Refrigeration Repair on a Continental Reach in cooler that is icing up. Found Defrost heater to have failed. Recommended Commercial Refrigeration install to replace the defrost heater.
Commercial Refrigeration Repair on a manitowoc Ice Machine that. Found multiple problems The drain was plugged, The drain also needs to be extended to the floor drain instead of draining on to the floor, And the compressor contacts and wires to the contacts burnt up Recommended Commercial Refrigeration Repair to unclog and extend the drain pipe, as well as replacing the compressor contacts and wires going into them.
Commercial HVAC repair for a LG mini split That is not supplying enough cold air for the room. found that the system is undersized for the space being cooled Recommended Commercial Install either installing another mini split or upgrading the first one to a bigger model
Commercial AC Repair For a AAON AHU that is not sending any cold air into the main space. Found Blower motor to have broken. Recommended Commercial AC Install of a new blower motor.
Commercial refrigeration Repair of a Scotsman Ice machine that wouldn't make any ice. Found compressor to be burnt out. Recommended Commercial Refrigeration Install To replace Compressor
Commercial HVAC Repair of a carrier condensing unit that would not supply any heat to the house. Found multiple holes in the Condenser. Recommended Commercial HVAC Install of a new Condensing system.
Commercial Refrigeration Repair of Follett Ice Machine that wasn't draining properly. Found that Drain was clogged. Recommended Commercial Refrigeration Repair to unclog the drain.
Commercial refrigeration repair on a silverking reach in freezer frozen solid. Found defrost clock not functional. Commercial refrigeration install new defrost clock.
Commercial air conditioning repair for a York Air Handler that is no longer working. Found the control board to be faulty and will no send any signals out to the unit. Commercial air conditioning install for a new control board.
Commercial refrigeration repair for a Hoshizaki Ice Machine that is no longer making any ice at all. The compressor is well past its life expectancy and no longer functioning. Commercial refrigeration install for a new compressor.
Commercial refrigeration repair for a Randell Reach-In Cooler that is not closing correctly. Door hinges are done for. Commercial Refrigeration install for a new set of hinges.
Commercial HVAC repair for a Carrier RTU that is only providing a small amount of air to the side series of offices off the main hallway. Found the fan to only be running at half speed due to a worn belt., Commercial HVAC install for a new fan belt.
Commercial HVAC repair for an American Standard RTU that is not sending any air to the main office space. Found the filters to be clogged and will not allow air through. Commercial HVAC install for a new set of filters on all RTUS
Commercial air conditioning repair for a Trane RTU that is sending little cold air to the main sales area. Found the unit to have airways blocked by clogged filters and restricting airflow. Commercial air conditioning install for new filters.
Commercial refrigeration repair for an Ice-O-Matic Ice Machine that is producing no ice. Found the thermostat to be faulty and the unit will not respond without it. Commercial refrigeration install for a new thermostat.
Commercial refrigeration repair for a Bohn Walk-In Freezer that isn't running cold enough. Found the fan to be down and the air not circulating. Commercial refrigeration install for a new fan motor assembly.
Commercial HVAC repair for a Lennox Condensing unit that is completely down and will not respond to any calls for heat. Found the unit to have a blown fuse. Commercial HVAC install for a new fuse.
Commercial HVAC repair for a Carrier RTU that is sending very little air to the main dining area. Found the units fan to have a belt that is stretched and the fan is suffering. Commercial HVAC install for a new fan belt.
commercial refrigeration repair for Hoshizaki ice machine not working. found bad water level float. commercial refrigeration installation to replace water level float
Commercial Air Conditioning repair for a Lennox RTU that is providing no cool air at all to the rear loading dock. Found the units compressor to have gone down and will not come back to life. Commercial air conditioning install for a new compressor.
Commercial Refrigeration repair for a Delfield Reach-In Cooler that is running warm. Found a leak in the compressor. Commercial refrigeration install for a new compressor.
Commercial refrigeration repair for a Manitowoc Ice Machine that is making a lot of noise. Evaporator fan is the issue. Commercial Refrigeration repair for a new evaporator fan.