Medford Wellington provides comprehensive heating, air conditioning, refrigeration, sheet metal, plumbing and electrical services to commercial and residential clients in Braintree, MA.
We are available for service 24 hours a day. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Braintree, MA.
for Braintree, MA
Our Reviews by City
HVAC Service call. Preventative Maintenance service completed per contracted agreement. All requirements per seasonal obligations have been met. Any issues found during PM service have been brought to the attention of the appropriate personnel and have been defined as either a critical or a non-critical issue for their review. HVAC call is complete.
Refrigeration call. Arrived and found Walk In Refrigerator running ok at -5 deg. Defrosted large ice balls in TXV section/ceiling behind Evaporator coil/suction line at exposed piping with heat gun. Rewrapped exposed sections of suction line and drain line. Also replaced A419 temperature control with an etc temp control. Old A419 control was no good due to sensor probe had burnt on electric heater and had no display. Dialed in new etc for -5 deg. Call is complete.
Refrigeration and ice machine call. Attempted to take apart gear motor and auger. Had to have a SecoND person to assist in dissembling. After several attempts and oiling down the auger could not get it to separate from gear motor. Very rusted on auger due to lack of maintenance. Water quality poor. Had to take out as one whole piece. Used cleaning solution that were spares on site. Cleaned auger and evaporator section along with drains. Put the head through a cleaning cycle and also cleaned the shut and discarded 10 minutes of ice. Did find some heavy rust and stiff shuttle which can result in ice machine not shutting off which will create the hi-amp error code. After cleaning, confirmed operation of ice machine. Also replaced water filters that were on site for that ice machine. Location has water filters auto ship every 6 months but no one installed them in March or the September months. Ice machine ran entire time on site for other work. Will need to replace the shuttle asap. H
Refrigeration call. Picked up and installed new walk in cooler condensation pan. Cleaned all side panels, fan blades and guards. Verified no leaks with a gallon of water. Call is complete.
HVAC call. Picked up parts when order was ready. Returned and installed new flame sensor, electrodes. Used spare run cap on site from existing motor. Verified operation. HVAC call is complete.
Rtu #2 locked out. (Not fault code capable). Reset unit and had normal heating operations. Air filters/blower/main gas all ok. No outside damper issues with discharge air at 119 deg. Presently no obvious issues found. Monitored and cycled unit multiple times and operations were ok. As with rtu #10 which heat was also out on the same day. Its possible but cannot 100% confirm due to very high wind conditions last night and today may have caused a lockout. Heat is presently operational. Heating call is complete.